The maintenance and care of the slurry pump includes the following aspects:
1. The water pressure and volume of the bearing should meet the regulations, and the tightness of the packing should be adjusted (or replaced) at any time to avoid leakage of the shaft seal. And timely replace the shaft sleeve.
When replacing bearings, it is necessary to ensure that there is no dust and the lubricating oil inside the bearing components is clean. When the pump is running, the bearing temperature should generally not exceed 60-65 ℃, and the maximum temperature should not exceed 75 ℃.
3. It is necessary to ensure the coaxiality between the motor and pump, ensure that the elastic pad in the coupling is complete and correct, and replace it promptly after damage.
4. Ensure that the pump components and pipeline system are installed correctly, firmly, and reliably.
5. Some components of the slurry pump belong to vulnerable parts, and attention should be paid to the wear and tear of vulnerable parts in daily use, and they should be repaired or replaced in a timely manner. During the process of repairing or replacing vulnerable parts of the slurry pump, it is necessary to ensure correct assembly, reasonable gap adjustment, and avoid the occurrence of tight friction.